So I finished all of the electrical and I've run into an issue.
I'm running all of my lights on an existing 15 amp Circuit Breaker.
this breaker currently powers the Master Bedroom, Closet, and Master Bath.
which currently has about 5 outlets, a cieling fan/light, closet light, Bathroom GFI,
Bathroom fan, and Bathroom Vanaty light. I'm adding the 2 new outlets, 8 canned lights,
amd 2 wall sconces.
Here's my delema. The dimmer switch controlling the canned lights
has power going to the switch. Verified by an flow detector. However I cannot
get the canned lights to come on. After turning the power on, when I turned
the dimmer on, I heard a pop and the switch smelled of electrical burns... never a good thing.
so I swapped the dimmer out with a normal (mind you used) switch I had laying
around and still nothing... This is my layout. any input would help me out greatly!
PS the wall sconce set up works as planned and looks fantastic!