Got all the speaker/Cat/HDMI wiring done this week. Ran a conduit to the projector area and another conduit to the area behind the screen wall.
Screen wall area:
HVAC is the next step. Still haven't finalized the plan. Not sure if I need two supplys or one. At the moment, I'm only planning on one cold-air return which will be on the right wall of the theater towards the (edit: middle). Not sure where I could put a second cold air return given floor-plan constraints in the rest of the basement. Any ideas?
If I do have to run a second supply, I was going to run it in the rear soffit above the projector box in the direction of the green arrows below. It would be encased in DD/GG and stuffed with pink fluffy to make a soffit muffler:
The problem is that I'm going to have the conduit going down through that soffit into the projector box...
Will it compromise sound isolation to have the HVAC flex duct pressing up against the conduit as they both run through the soffit? I will plug the conduit with insulation, and of course there will be insulation within the soffit surrounding the flex duct.Edited by rs691919 - 6/16/12 at 6:53am