3 way CE dimmer problem
I am having issue installing a CE 3 way dimmer. I have installed plenty of dimmers in my life and this one is not normal. I identified the hot wire in box one, installed dimmer in that box, Wired hot to hot screw on dimmer. connected the two travellers and neutral. went to box two, identified load wire, connected load wire to black screw of a 3 way switch and two travellers to brass. tied neutral together. Dimmer turns on but only if switch 2 is in the on position. does anyone see anything thing different in the attached diagrams that makes my wiring way wrong?